Get Paid For Your Thoughts!
- Wiley (Food Quality & Safety’s publisher) is offering $200 to qualified food scientists who participate in research interviews about challenges facing the food industry.
Take the survey >
Clean-in-place (CIP) systems are used by food manufacturers to eliminate the soil load buildup during normal production. CIP systems vary widely in configuration, operation, and the level of automation. In many companies, plant, corporate engineering, IT, and their partner integrators are pitching in to create robust automated systems to improve CIP operations by reducing cycle times as well as reducing water and chemical usage. The techies are helping production in many ways by using the most current technologies for computers, process controls, instrumentation, software, networking, and security in CIP. These platforms are being integrated into comprehensive systems to provide new levels of efficient and effective CIP operations, data capture, and real-time information analysis. Let’s explore the tools making automation in CIP contribute more to the bottom line than ever before.
CIP Systems: Different But All the Same in the Eyes of Automation
Configurations vary for CIP systems. They typically include self-contained skids; kitchens with large tanks for single CIP systems; and kitchens with large alkaline, acid, sanitizer, and recovery tanks for simultaneously servicing multiple CIP systems.
Whether a CIP system is a skid or kitchen, it can consist of the following.
- One Tank – combined rinse and wash
- Two Tank – separate rinse and wash tanks
- Three Tank – rinse, wash, recovery
- Four Tank – any combination of rinse, wash, alkaline, acid, sanitizer, recovery
- In-line or in-tank chemical dosing for one-pass chemical usage systems
- Separate chemical tanks for alkaline, acid, and sanitizer for multi-pass chemical usage
Components common to the variety of CIP systems include water supply source; supply pump; supply-side heat exchanger and temperature transmitter; tank inlet, outlet, and recirculation valves; chemical addition pumps; and chart recorder, either paper-based or electronic, to record, at a minimum, temperature over time.
CIP operations can be successfully run with this configuration, although a high degree of manual control, constant monitoring, and intervention is necessary to insure effective and safe operation. Production usually finds it very difficult to maintain consistency of chemical concentrations, wash temperatures and times, and rinse water quantities. Worse yet production may routinely over compensate the operation by adding more chemicals to insure minimum cleaning requirements are met or running at higher temperatures, longer wash times, and greater rinse water quantities; all more costly to operations.
Better Instrumentation and Controls
Manufacturing can significantly increase efficiency and reduce operating costs for CIP by enhancing systems with additional components. More robust CIP systems will have the following components.
Supply side flow transmitter – rinse and wash steps can be precisely controlled by totalizing the liquid quantities delivered to each CIP circuit.
Variable frequency drive on the supply pump – supply side flow rates can be precisely controlled with a loop control tied to the flow transmitter above. The benefits gained are ensuring line circuits achieve minimum liquid flow velocities for surface contact in the various pipe diameters, and sufficient flow through spray balls for tank circuits.
Supply side line pressure transmitter – monitor point to detect if an obstruction in the circuit is present when pressure is too high or a break in the circuit exists when pressure is too low.
Level transmitters or level probes on the tanks – used to signify when action needs to be taken; especially when low levels are reached before or during a CIP operation.
- Fresh water tanks – refill to a mid or high level
- Chemical tanks – add more water and the appropriate chemical to have
- sufficient solution for the appropriate wash step(s)
- On high level – stop filling the tank
pH transmitters for alkaline and acid tank makeup – monitor point used when combining water with the alkaline and acid chemicals to the desired concentrations and pH levels.